1. Material composition
This is a water-based fire retardant paint and is manufactured by a mixture of selected mineral particles from a low-permeability elastomeric binding compound. The product can resist fire from 2 to 4 hours with an extremely simple construction solution, just spray paint on the cleaned duct surface. Thicknesses range from 0.7mm to 1mm, allowing ductwork to be designed in a narrow space with high material requirements and low maintenance, especially in harsh environments. The finished system is tested to BS476 Part 24 and ISO 6944 standards up to a temperature of 1,133°C, and is certified by LPCB, UL and Vietnam Fire Department.
- Fireproof material is a water-based coating mixture containing mineral particles
- All fireproof ducts made from galvanized steel, stainless steel (or steel pipes with antirust coating) must be tested to standards and protected with a flame retardant coating, in the form of paint. room will not be accepted. The air hose is manufactured in parts and connected by fireproof tested tooth and glue. Every time it is fitted, if required by the engineer, it shall be pressure tested according to DW144 and/or SMACNA in accordance with the duct pressure classification. The protective coating is at least 0.7mm thick (after drying).
- Fireproof ducts must comply with BS476 chapter 24 (1987) and ISO 6944 (1985) for 2 hours for stability and integrity for both internal and external duct testing. The smoke exhaust duct must be kept at least 75% of its cross-section during 2 hours.
- All symbols for the ventilation system shown on the drawings must be designed to resist fire within 2 hours as prescribed by the local Fire Prevention and Fighting Department.
- All seals and silicones must be non-flammable and should be supplied by the same manufacturer.
Application of fireproof paint for smoke extraction systems, pressurizing stairs, exit corridors, kitchen chimneys